See Our Social Media Links for More Project Pictures and Information
Bunch of defects here didn't help the situation. Had the EMT been strapped properly the wires may not have severed when the conduit was hit. One receptacle was arcing against the box and every nut was cross threaded at the connector in each box we opened. Loose connectors as well. No wonder this conduit network lost it's bond. Will be tracing through the connections to find the missing bond connections after we fix the damaged parts. It's amazing how many defects one can leave on one simple run.
We get requests to replace fluorescent fixture ballasts all the time. For not much more expense you can replace the whole fixture with an integral LED one. No more leaking and buzzing ballasts and with the bonus of energy saved. Ask us about dimmable options for offices as well. Have different brightness for different rooms along with even more energy savings. Ask us about zoned lighting control as well.
When you show up for finishing and the owner has decided to flip up the tabs on the electrical boxes. I wish I saw the look on my face when I discovered this and looked around to see they were everywhere. We made it work for him as always. Anyone see this move before? Never knew I had to put a provision for this in my contract.